OK ,I have a 200amp service residential.I have a out building/workshop with a 100 amp main breaker panel installed. Now can I run 3 wire service to it?Bond neutral to can. Do I place a rod there or not? Do I run 4 wire and place rod? I re read some past threads but need alittle reassurance.Thanks in advance. using direct burial cable pvc conduit.
Not that I`m aware of at this time.I read 250.32 Not clear on the single branch part.Electricians here say you can run three wire but the best way would be go with 4 wire and the rod.Just would like to better understand if three wire is permisable in this situation legally. But also personally I`m lean towards the best way if it is better.
Re: detached building (again) sorry#88297 05/27/0404:04 PM05/27/0404:04 PM