I require my employees to install all recepts by hand. Common screwdriver and strippers only... No sidecutters allowed, no cordless drills (I do let them use a drill to mount device in box). What do you allow your help to do? Using cordless drills to wire a device scares me a bit even if it is faster.
'66 and arsegee: I am with you no power tools to install receptacles. Yes we are suppose to torque the screws on receptalces, since getting my new Klein Torque screw driver, and the the required torque for a receptacle is 9-12 in-#, this is according to Hubbel, I have realized how much we have a tendency to overtorque everything. I usually set the driver at 12 in-# and it dont take much to 'Snap-it' and your done it holds it snug but not overly tite. -Mark-
Re: Helper 101, how to install a receptacle#9767 05/13/0205:19 PM05/13/0205:19 PM
Myself, I use a cheap black and decker cordless screwdriver. They sell them at home depot for $19.99. You can really get a good feeling at how much torque you are using with it. Not to mention in speeds up the installation process by 40-50%. As for a helpper. Well let him practice on some junk recep's untill he gets the feel for it. Then I would let them use it. But as for a cordless drill. I would never use it, too past and you do not feel how much torque is being applied.
Re: Helper 101, how to install a receptacle#9770 05/13/0211:52 PM05/13/0211:52 PM
CRW, through the years I have seen so many guys that strip their wires with their pliers and make the loop. One of the old timers I worked for use to rag me about using strippers. One time I pulled apart some of his work and showed how he was slightly nicking the conductor and thus lowering the ampacity. He never said another word about it but he still uses his sidecutters to strip with.
Re: Helper 101, how to install a receptacle#9773 05/14/0211:47 PM05/14/0211:47 PM