Is there any code compliant method of connecting from schedule 40/80 to liquidtight conduit? I'm not looking for a single "tweenie" connector, use of a junction box would be fine. An insulated grounding conductor would be run the full length.
I saw that as a possible combination. However, I wasn't sure that the manufacturer of the liquid tight connector meant for the connector to be used with other than a metal box where a metal locknut would be used on the inside of the box. Since the rubber washer on the liquid tight connector is normally locked tight by the metal lock washer on the inside of the box, I wasn't sure that the same would be true if the connector was made tight into the pvc female connector.
Sounds like it is ok, then.
#95869 - 10/15/0508:52 PMRe: Liquidtight to Schedule 40/80
We can never assume that there will never be moisture entering the conduit. PVC conduit leaks quite well. Take the gasket and put it in the junk drawer for the time you'll need it when the manufacturer shorts you. Arrange the conduit run to drain. Special fittings are made for this purpose. Use a "T" condulet, with the drain at the bottom of the "T".
#95871 - 10/18/0506:12 PMRe: Liquidtight to Schedule 40/80