Yep, too many bends. Count the 90's.. I count 7. I'll try to get another picture of a different building in the same complex that I happened to spy today with 585 degrees of bend and no pullbox. These guys are classic..
Re: Can You Dig It?#111629 01/12/0710:27 AM01/12/0710:27 AM
That box looks to be at least a foot down. IMO, there's a world of difference between a light covering of bark (or gravel) ... and placing it that far down.
I suspect that the low voltage guys will no longer consider this buried box acceptable after the first service call.
Ironically, despite the gasketing, I find that dirt and water still manage to get in those boxes. The use of an "N-9" handhole would have been a better solution. (An "N-9" is a fiberglass tubular handhole, with a mid and open bottom. Overall size is about the same as a 5 gallon bucket).
[This message has been edited by renosteinke (edited 01-12-2007).]
Re: Can You Dig It?#111630 01/12/0710:18 PM01/12/0710:18 PM