Can anyone clear this up? Section 200.6(A)states that the grounded conductor must be identified continuous. If you read further to 200.7(A)(3)states you can identify at terminations. This contradicts itself. Any help please.
I swear, it's all a conspiracy to sell us 4 spools of #6 cable when we really only needed 1!
tell me about it i have the same thing as well and end up get 4 or 5 spools depending on what area i have to do.
the only issuse when i get to larger wire size like 2/0 and larger normally i useally have color coded tape to use it but i think i did see one wire manufacter do make the larger wires size in color in bulk roll now but not sure if that is the fact .
Merci , Marc
Pas de problme,il marche n'est-ce pas?"(No problem, it works doesn't it?)