What do you do with the neutral wire of a 14/3 romex when the two hot wires are circuits for the bedrooms?
I bought four Fault Protectin Breakers for my four bedroom circuits but when I went to install them I noticed they were run with 14/3.
Each Fault Protection Breaker has a neutral pig tail built into it to land in the neutral buss bar. You are suppose to take the neutral from the homerun directly to the breaker neutral terminal.
But I only have one neutral for two circuits.