NEC Article 100, Definitions. Branch circuit, multiwire. The definition describes a shared neutral. As far as I know the new Code does not prohibit the use of a shared neutral. In some cases, for branch circuits feeding computer equipment it's better to run two 2-wire circuits instead of one 3-wire circuit.
[This message has been edited by Frank Cinker (edited 06-02-2002).]