Just finishing up a new house, have all the power on, plug in the first smoke and it trips the AFCI. I've had smokes on these circuits before with no problem. Tryed a different smoke and a different AFCI, no help. Any ideas?
The NEC says all outlets of any kind in a bedroom must be on AFCI. Here in Idaho the State has issued an advisory that it and all local AHJ's will accept smoke detectors in bedrooms without AFCI protection until such time as the technology catches up to the reality.
Well, no. There is no required dedicated circuit for smoke detectors in a dwelling in the '02 NEC. I don't do houses anymore, and while I think that a seperate smoke detector circuit is good planning, most of the time it's a cost issue and we all know how that goes. I have heard reports of this problem with AFCI's and smoke detectors from a lot of guys. I think Idaho has the right idea, for now.
Re: Smoke Detector tripping AFCI#49555 03/10/0503:47 AM03/10/0503:47 AM