By looking at your dash I see you've obtained all the items on the scavenger hunt list.
What's with all the grounds? Looks like they aren't even compressed into the connector. Are there two ground rods there?
I like the color coded breakers. I did something similar in my house so the wife would know which ones are lights, outlets, etc, etc. And which ones not to mess with... Can you tell us more about the color coding.
thr scavenger hunt was fun but I did not win,you should see the boss' van. yes the pannel looks nice but you can tell that the guy who made up the pannel was not the same one who did the pipe work above the droped cealing"drunken monkey piping". yes there are 2 ground rods one rod is done properly the other one has a bonding clamp on it.
the color codeing is for the employes "only turn off the green ones they are the lites".
Bob: Good shot! OK, two rods?? not bonded together??? Pipe clamp on rod, inproperly used?? Distance between rods?? Paint encrusted pole feeder repair?, more of that around then the ones done correctly!
The excuse for the 4" round/cover...someone moved something, note the tele ell fitting. My guess, it goes to a relocated sign!
The FS box? cable feeding it, brick wall....handyman hacker.
Retail bldgs are notorious, including the neighborheed pizza joints.