I hope this isn't too dumb for the forum, but here goes:
I worked with an electrician who was big on directing process and not too big on explaining theory. Most directions were explained by "Because I said so."
I've noticed on forums here repeatedly the concept that you do not terminate ground wires and neutral wires in a panel on the same terminal strip. The old boss is retired and moved away, so maybe one of you pros can explain to me what the deal is here.
I should mention that we worked exclusively on residential.
Last edited by Retired_Helper; 08/25/07 03:50 PM. Reason: Duh, left out words!