How do you guys terminate receps and switches? Do you make a loop and go under the screw or do you push into the tab on the back? Ive notice that more folks are using the pressure type connectors over wire nuts to terminate the neutrals. Again what do you all think. Is it a time saving aspect!!! And do you think you would get just as good of a connection?
The likes of the Wago Wall-nut aren't available at my supply house's except for samples, that everyone leave at the counter... So, they are not really available. I really like the idea but some versions don't have the nessesary versitlity of capacity for stranded/solid #12 for 5 conductors. Not sure if I would trust a 3/4-wire neutral connection with them. How-ever, some of those European screw-type pressure connector though... Wish they made them for applicable use here.
In terms of speed, you still have to strip the wire, and put one on. One could reduce the fatique of the wire nut by using a wire-nut-driver, or my favorite a wire-nut-driver on an impact wrench.
Mark Heller "Well - I oughta....." -Jackie Gleason
Re: whats your opinion#53306 06/21/0506:16 PM06/21/0506:16 PM
Backstab outlets should be outlawed given their well established reputation for causing problems. The problem is worse where they are used for feed-thru but even when conductors are "tailed out" there's a fire hazard created if say a portable space htr. is connected.
I'm surprised that the NEC hasn't already addressed this issue by now.
Re: whats your opinion#53308 06/21/0507:10 PM06/21/0507:10 PM
Using the "back stabbing" method of terminating devices will guarantee one thing . Your guaranteed to have problems in the future with them ! I only use the screw and anyone on my jobs must use the screw. Wirenuts and pigtailing is the norm.
Re: whats your opinion#53309 06/21/0509:36 PM06/21/0509:36 PM
Screws and wirenuts.. I have never even seen a pressure connector at my shop, but I do get chided from time to time by the guys who came up in the trade as piece workers or resi track guys for not sticking switches and recepts- at which point I just laugh and mutter something obscene under my breath. I loathe sticking- nothing but a royal pain when you have to take things apart and you are just asking for a broken wire, stuck switch, or short because the guy who stripped the wire left too much exposed, although I do admit- it is "faster" for what that's worth (not much in my opinion, considering the trouble sticking causes..) This may just be personal to me, but how many of you also screw down the unused terminals on recepts? I always do- it just takes a second more and gives you a little more clearance between that neutral or hot wire & the ground in a multi-gang box. This is another little quirk that gets the piece-workers and tract guys shaking their heads in incomprehension, but (as far as they go..).. who cares!
Re: whats your opinion#53310 06/22/0506:59 AM06/22/0506:59 AM
Thanks guys for your feedback. I would have thought that the subject would have been somewhat divided. But this was very interesting that so far everyone that has replyed, is steadfast against using anything other then the screw terminals. This proves one thing to me, that there is still alot of guys in the trade who are still shooting for a quality job vs a quicky with a paid invoice.
Re: whats your opinion#53311 06/22/0509:41 AM06/22/0509:41 AM
there is still alot of guys in the trade who are still shooting for a quality job vs a quicky with a paid invoice.
That's why I like this place
The wago type pressure connectors as used on ballasts are very good for lighting, I use them here in the UK for wiring things that are unlikely to need maintenance work done on them, and are generally low current, anything higher current gets terminated the long-winded way, it takes less time in the long run because you don't get so many callbacks.
Re: whats your opinion#53312 06/22/0511:52 AM06/22/0511:52 AM