I am going to run a dedicated circuit to a hot tub (60 amp) load center/GFCI disconnect.
Can I use cable type THHN or do I have to use something like USE? Would this be classified as a service wire when carrying power to the disconnect? Can I run more than just the spa off of the feeders to the spa disconnect?
Hi, I did not see in your post WHERE the spa was located? That is VERY important. You are possibly talking about two different wiring methods. Forget about using SE cable. What is this THHN cable you are talking about? Multi-Conductor Cable for a cable tray or conduit?
What is your experience level? Are you licensed at all?
Spas are tricky and expensive to wire up.
There is more to this than you may have first thought.
[This message has been edited by mustangelectric (edited 11-22-2004).]
Electricity has no respect for ignorance!
Re: intresting post on other site#45279 11/22/0409:15 PM11/22/0409:15 PM