Thanks Greg. Specifically this extra circuit will be for two counter top receptacles in the laundry and one outdoor receptacle, all 20 amp GFCI protected. What got me thinking about it is the argument about the kitchen SABC circuits, no matter how many you provide after the required two they still cannot have other outlets except dining, nook, pantry etc. as I understand it, and as my jurisdiction enforces it.
Last edited by BigB; 04/16/15 10:28 AM.