Asking from all the experienced electricians who have been in the trade far longer that I have...What is the best way to make a hole in a brick wall for a receptacle box where a homeowner wants a GFI installed outside? Do you mark the wall for the dimesion of the box and then drill several holes with masonary bits and then chisel out the brick until the box fits? What kind of box is the best to use? Thanks!
I do exactly what you stated using a single gang mason box. I then also fill in the gaps using mortar. The dimension of the box is usually half that of the brick, so you only have to drill one side. I would use 1/4 inch bit or smaller.
Jesus may have been a capenter,but God was an electrician.Genesis1:3
#97751 - 03/20/0612:05 AMRe: Installing a GFI on a brick wall
I cut in first with my 4" diamond blade to make the outline about 1/2" deep, then I use my 2" coring bit on my rotary hammer to remove most of the material, finishing it off with a chisel. If the box is outdoors I will get some mortar to set it, but if indoors I will just mix up some 20 minute joint compound since I keep that on the truck...it holds like you wouldn't believe.
#97752 - 03/20/0603:00 PMRe: Installing a GFI on a brick wall
So basically, knock out a hole just a little bit bigger than the box and then mortar around the box to keep it in place? Is there a type of box that will fit in the hole and tighten down on the brick? Is there any kind of mortar that comes in a tube that can be put around the box from a caulking gun or will I have to buy a small bag and mix it? Thanks
#97753 - 03/20/0603:12 PMRe: Installing a GFI on a brick wall
I use my 4 1/2 grinder with diamond wheel to cut the outline of a masonary box(mudbox) then finish the job with a masonary drill . I use a bosch bulldog , I have a small chisel that fits right into the drill and this works great ! I then pull cable,mc,greenfield etc out and attach to box, then fill entire hole with mortar,then push box back into hole, clean up and touch up around box. wait till set and trim out.
#97754 - 03/20/0605:57 PMRe: Installing a GFI on a brick wall
I have seen some pre mixed concrete repair products at Home Depot. They would probly work fine. I keep some of those small pails with covers that joint compound comes in and store dry mortar in one and dry joint compound in another. That way I never have to open a container and find out it has dried out or froze. If your truck doesn't have the room just keep em in your garage and remember to load them up on days you will need them.
P.S. I've heard expanding foam works pretty good too.
#97756 - 03/21/0612:36 AMRe: Installing a GFI on a brick wall