Guy's I've wired several new and remodeled homes and have had them all pass. But it never fails that I'm always second guessing myself when it comes down to laying out my circuits. (Will I have enough spaces in the panel, am I over loading a circuit, This circuit only has a few drops and is not loaded when the one next to it is maxed out, etc.). These are some of the questions that I wonder about often. Do any of you have some tricks that you use that may help me get through these types of stumbling blocks.
Just take a few Hours, prior to beginning the rough Installations, and figure out what to do.
Get a set of "Clean" Plans - at least "D" size media (24" x 36"), and layout your Circuitry on paper first.
Count up the circuits for Panel Requirements (AKA spaces and frame types), and identify them on both the plans and the NM cable end (at the panel). This helps out logistically and makes it easier to enter circuit data in a Panel Directory.
If you can get 2 or even 3 "Clean" Plan Pages, that would be best. Use colored PENCILS for drawing circuitry / Homeruns, where multiple "Types Of Circuitry" will be used (i.e. Lighting = Blue, Gen. Receptacles = Black, Kit. ckt = Red, etc.)
What I mean by "Clean" sheets is to find plan pages with the least amount of stuff printed on them, so the Floor Plan (Base Template) is easilly seen - plus there will not be so much confusion between what you write/draw for As-Built data, and notations text printed on the sheet.
"A" Sheets might have something rather clean (like a Foundation plan, or similar), and if there are any "P" sheets, these would be the cleanest.
One last thing, make use of Multiwire Circuits as Homeruns where ever possible. (ohhhh, this is going to draw some flack!)
Scott " 35 " Thompson Just Say NO To Green Eggs And Ham!
When in new const. we kept it simple for recpts no more then 10 per circuit. Lighting was pretty much the same execpt when low voltage cans are used they draw little to no amps so load them up and buy the good dimmers and your golden. Kitchens always home runs for each peice all in 12 NO 14 ever!!! ovens get whats needed. The only 14 in my kitchens is lighting and u/c lighting. JUst keep it simpole 10 items and no more and its never failed me yet. I also beleive in keeping lighting and power on there own circuits.
Re: resident layout#51286 05/07/0511:48 AM05/07/0511:48 AM
I have done homes as large as 14000 square feet, and i find that keeping each room to its own circuit is best. Especially since most costume homes floor plans always seem to change. This does not include rooms that have multiple recess cans, obviously some rooms may need more than 1 ckt. I try to keep 10-13 openings per circuit. Also, In reply to scot35, I will take a set of plans to a printing place and have them remove all but the exterior wall and then I fill in acording to my layout....cost is 5$per page but it is worth it
Re: resident layout#51287 05/08/0501:09 AM05/08/0501:09 AM
hey larry, was just wondering how small the house was? and what you charged for wiring?? I am bidding a 2500 sq foot home and just want to get an idea of my price with others around the country,,, I am in upstate ny.. thanks.............. wayne
Hope I'm not jumping the gun here, but it would be kind of hard to keep the bedroom lights and receptacles on a separate circuit, unless you're prepared to add extra AFCI breakers for them. May not be too bad for a small house where you can get by with two breakers, but a larger house, it could get pretty expensive. Just a thought. Steve....