Can a standard 3 pole disconnect switch be used to switch 2 phase conductors and 1 neutral. My concern is the lack of accurate synchronization of the blades making to their respective contacts. If the neutral blade makes last it could cause over-voltage in the phase to neutral loads. Seems like the neutral blade would have to make 1st and break last. What about a 3 pole molded case circuit breaker ?
What do you think?
Thanks in advance.
Last edited by Stu T; 09/01/13 02:24 AM.