So I started going back through some of the basics this week and its good because I'm noticing some stuff I've probably skimmed over before.
My first question is regarding 406.11 "Tamper-Resistant Receptacles in Dwelling Units In all areas specified in 210.52, all 125-volt, 15- and 20-ampere receptacles shall be listed tamper-resistant receptacles."
So, I believe in TR receps, but I admit I don't use them all the time, simply because they're annoying as hell if you're the end user. But is this really saying what I think it is? Are all receps in "every kitchen, family room, dining room, living room, parlor, library, den, sunroom, bedroom, recreation room, or similar room or area of dwelling units" (from 210.52(A)General Provisions) supposed to be TR? Am I dumb or is this saying that? Do you guys always install TR's? I'm pretty sure it's not the norm here. I know if I just go to the supply house and purchase a 20A recep it is not normally TR. Any other info I'm missing here or is this exactly what I read it to be?
Ok, my second question I might know the answer to, but I'll ask anyway and see if I'm thinking right. It comes from the exception found in "406.8(B)(1) 15- and 20- Ampere Receptacles in a Wet Location. 15- and 20-ampere, 125- and 250-volt receptacles installed in a wet location shall have an enclosure that is weatherproof whether or not the attachment plug cap is insterted." OK, so that one is pretty common knowledge, but I've never heard of the exception and not sure I fully understand the logic behind it. Exception reads; "15- and 20-ampere, 125- through 250-volt receptacles installed in a wet location and subject to routine high-pressure spray washing shall be permitted to have an enclosure that is weatherproof when the attachment plug is removed." Maybe I'm reading this wrong, but is this saying that you can put NON in-use covers in areas where there is routine high-pressure spray? I would think it would be the opposite, wherever there is high-pressure spray there should be in-use "bubble covers" installed. The only thing I can think of is that maybe it's because the bubble covers are not set up to keep out water from below? Is that correct? Maybe coupled with the assumption that routine high-pressure spray probably means an environment more likely to have "qualified personnel" running any equipment? Any of that correct?
I appreciate any input. I've never been one to be ok following the rules just because they're rules. I want to understand why as well, so hopefully you guys can shed some more light on all this for me. Thanks,