woah, that's a good price.
The one I'm eye balling is a FP from Canadian Tire. It's $250.
I haven't checked the wholesaler yet. They carry SqD and Seimens stuff.
Cool ya, thanks, it makes sense to treat the Generator like a service, or a sub-panel (with respect to neutral), depending on it's grounding.
I would like a section in the codebook that would clarify Generators.... even though all the other general rules do
I asked an inspector my question about the breaker from the main panel. He said it's just like a disconnect, so 30A is fine. The branch circuit breakers will do their own job.
Now I get it all. Thanks guys... I feel taller or something.