Handyman 1 (the previous homeowner) decided to replace an ungrounded receptacle with a grounded one, so he put a wire from a cable clamp screw to the new recept. OK, not code-compliant, but better than usual.
That is, if this house wasn't wired with NM Cable.
Thankfully inspector 2 (Falls Twp.) caught it and Handyman 2 (the "fixit so we can sell it" one) removed it.
Ian (Hope I'm doing this right) A.
Last edited by Trumpy; 11/01/0704:29 PM. Reason: Edit thread title
If you would like to start a photo thread for the Violation, Discussion or Nostalgia areas you can start it in one of the General areas (ie General, NEC, Non-US etc.) and it can later be moved by a Mod into the appropriate photo area.
Besides, it means that all the photo threads are all kept together in one area of the site and makes things easier to find.