Handyman 1 (the previous homeowner) decided to replace an ungrounded receptacle with a grounded one, so he put a wire from a cable clamp screw to the new recept. OK, not code-compliant, but better than usual.
That is, if this house wasn't wired with NM Cable.
Thankfully inspector 2 (Falls Twp.) caught it and Handyman 2 (the "fixit so we can sell it" one) removed it.
Ian (Hope I'm doing this right) A.
Last edited by Trumpy; 11/01/0704:29 PM. Reason: Edit thread title
If you would like to start a photo thread for the Violation, Discussion or Nostalgia areas you can start it in one of the General areas (ie General, NEC, Non-US etc.) and it can later be moved by a Mod into the appropriate photo area.
Besides, it means that all the photo threads are all kept together in one area of the site and makes things easier to find.
Let's face it, these days if you're not young, you're old - Red Green