4-gang with bundles of wires, switches not grounded. No outlet on counter. Romex in plumbers pvc. 25' of unfused cable hanging on plumbers strapping. A mess inside and out of panel. Central vac flopping in the return and the 90 not connected. No staples, meter sockets not level. I don't know what you guy's want, it works don't it. And yes there was a rough and finish inspection.
Pic 9 is most frightening! Take look at those Engineered Lumber joists. Some gormless fool has drilled through the OSB webs right by the flanges, and even put in some extra holes for future requirements!!!!
I'd get me to a lawyer.
[This message has been edited by electure (edited 04-10-2006).]