His business card is in the bottom of the panel, but we must protect the identity of the guilty as well as the innocent , another thing that is a problem is a lack of circuit directories in the panels.
Do we see at least two breakers with green wires tapped off them???
Hopefully they are re-identified at the other end?!?!?!
DIY'er? Or, colorblind person did the wiring?
"Green only as grounding conductor"-what is the code article? 310.12 Conductor Identification (C) Ungrounded Conductors? ("...shall be... clearly distinguishable from grounded and grounding conductors.")