Wow: two posts in under two minutes!!!
I'll have to show you the rest...you'll die. Nuetrals on hots, hots on nuetrals, bonding on the load side ( A real fire hazard in this case...think about it), Schedule 40 lateral riser, no bonds on metal raceway with GEC, etc...
Heres the best part...they used a bond bushing on the panel. What exactly are tehy bonding here...the locknut?
I'll hopefully get some more up tonight or tommorrow.