Well to start with the obvious, unprotected conductors dubble-lugged to the service conductors, one is white and not re-identified, romex entering with no protector through an unsealed knockout in an apparently 3R enclousure, probably a couple more I'm missing. And there's the non-code issues of neatness and the fact that it's a FPE
[This message has been edited by Elviscat (edited 11-14-2005).]
Re: What's Wrong With This Service??#109623 11/15/0502:05 AM11/15/0502:05 AM
This could be a main, no breaker is required if there are less then six breakers (4 full sized single poles, 2 double poles), plus the three wire feed and the EGC seems to me to indicate a main panel, perhaps you could clear this up yaktx?
Re: What's Wrong With This Service??#109630 11/15/0510:21 PM11/15/0510:21 PM
Yaktx: Where's the EGC connected, since it doesn't look like it's headed for the ground?
I assume you are referring to the GEC, meandering off to the right in an upward direction? The answer is nowhere. The house was replumbed and the plumber never replaced the ground clamp. The deadfront was there.
Nearly all Stab-Lok panels had one row of upside down breakers, which was legal at the time.
The lack of a main breaker does not mean this is a subpanel. I assure you the meter was right above this panel. In this case, it is service equipment which is in violation of 408.36(A). This service appears to be from the '70s, and my vintage NEC collection tells me it was illegal then, too. Nevertheless, many such installations were approved in my area during this time.