Triple, the conductor from one electrode to another is not a GEC.
The GEC runs from the panel to some point of the grounding electrode system.
The conductors that connect multiple grounding electrodes together are bonding jumpers. 250.64(C) does not apply to these bonding jumpers.
Here is a picture from the handbook showing different ways of connecting the grounding electrode system together.