(submitted via Joe Tedesco)
We had an incident at work where an employee was dispatched to secure a loose wall pack. The employee went to inspect the light and was shocked when he touched the fixture and could not let go, and was rushed to the hospital. When he came back to work he was fired for not working safely.
He was shocked because the conduit was broken loose from the fixture and a line wire was partially stripped. The conduit was the only ground.
I was wondering if it is a violation of any codes to not have a ground wire running through the conduit or from the conduit to the fixture.
If you cant answer this can you point me in a direction to help me find out.
I work in Illinois.
[This message has been edited by Webmaster (edited 06-06-2004).]