A service lateral originating at the Power Company pad mounted transformer secondary terminals will be installed in PVC. Voltage system is: 277/480V, 3Ph, 4W.
Am I correct in thinking an equipment grounding conductor is not required from the transformer to service disconnect.
I don't think it is a requirement.
[This message has been edited by Frank Cinker (edited 10-15-2002).]