No 11 is freakin me out...man. 1. Home made bussing 2. Lack of proper clearance through both boxes 3. Grounded conduit right in front of the small oaked-in box. 4. that looks like a HV transformer thats been cut into.
This reminds me of some work I saw in Palm Springs on the wind farms.
#112303 - 12/14/0502:24 AMRe: Photo Series (Page 1)
Wow 4-1/2 years since this post was originally posted.
Is this part of an OEM machine or piece of equipment? I think that some OEM shops will install the wiring any way they want and slap a UL label on it and get away without following the same installation methods that we are bound to when the wiring is field installed.
I am sure that the OEM shops dont have actual electricians doing this work.