Seems that one of our clients decided to relocate their air compressors (Ingersoll-Rand screw type) and poured a nice, thick concrete pad on the south side of their mill. The 2" conduit LB feeds conveyors just beyond that new pad. I guess that's how they make sure that they don't dig up the conduit with a backhoe?
Yep. I figure it's wire-tight now, too. Although I suppose that as long as we can get a porta-band in there, it's still servicable, right? Anyone know if the code requires that both screws actually be in the removable portion of a cover?
Actually, my concern is that most LB's are made of zinc, or aluminum, neither of which will long withstand being eaten up by the alkali in the concrete. I do not believe that such bodies could ever be listed for such burial. The LB must be "accessible." As NEC defined, that does not include the use of a jackhammet to reach it.