I just got a red tag for not having a main in a subpanel in a residential detached garage. Panel is a C-H 4/8 MLO with 2 circuits installed. AHJ is using 225-31 as the reason.
Is anyone elses area requiring this. I guess I was thinking 6 or less breakers did not need a main.