It looks like someone pulled the feeder as a 1Ø
As in thinking it was a 120/240V panel? Sounds plausible from the feeders there. I don't know how long that feeder is, but how hard would it have been to just pull in another blue conductor and do the job properly?
Any idea what that transformer on the top of the panel is feeding? And what's that gizmo to the right of it?
Even if the xfmr secondary is low voltage, the open wirenutted splices outside the panel are still very messy and I don't think much of the mounting and wiring method.
[This message has been edited by pauluk (edited 07-22-2004).]