photos courtesy: Harold Endean and SonsOpen box:
This box had no support, was laying on the ground, no GFCI receptacle, no KO seal, and the UF wire is subject to physical damage. Broken receptacle:
This box has no support, no ground fault protection, Type UF wire subject to physical damage, the wrong style of UF connector on top of the box!
Also, this box was used to run a submersible pump in the water fountain next to it! Broken receptacle:
This box was supported by one pipe coming up through the concrete.
This box was located in the pathway between the holes on the golf course. Also there is no ground fault protection. Open wires:
This one speaks for itself. People walk on the white stone
path, I don't know if there was any current in the wires. (I hope not.)
[This message has been edited by Joe Tedesco (edited 09-03-2002).]