I believe a "blowout coil" uses the actual magnetic field generated by the coil to extinguish the arc by repeling or pushing it away from the contacts. I have a detailed explanation in a book somewhere. I'll look it up.
[This message has been edited by Redsy (edited 05-10-2005).]
Re: Blowout#93274 05/11/0511:34 AM05/11/0511:34 AM
Sorry, dhoule, my computer has been in the shop for 10 days. Basically, the contacts are mounted on the middle of curved strips called horns. As the arc forms across the contacts the magnetic field of the blowout coil pushes it up the curved pieces of the horn, which, since they are curved outward from each other increasingly lengthens the arc to the point of which it can no longer sustain, and therefore extinguishes.
This is in the book, "Electric Motor Control" by Walter Alerich. Published by Delmar.
[This message has been edited by Redsy (edited 05-20-2005).]
Re: Blowout#93276 05/23/0508:37 AM05/23/0508:37 AM
An old (1920s) device had a spring loaded fuse-wire which was contained with carbon tetrachloride in a glass tube. The chemical vapor doused the arc as the melted fuse-ends were whipped apart. Used only on high voltage/low amps instrumentation transformers where the cost of a full breaker set was not economically justified. Alan.
Wood work but can't!
Re: Blowout#93279 05/24/0508:53 AM05/24/0508:53 AM