i installed a sunhouse storage heater and everything was working fine when i left it, but now the heater has stopped working. there is no voltage at the load side of the thermostat at the top of the heater, but there is at the supply side. i know these things have thermal cutouts but im not sure what im looking for, so i was wondering if somebody had a picture i could get some idea from and how to reset it if its tripped.
Matt, There should be a small resettable switch on the front of the thermostat. This is usually wired between the main feed wire and the line side of the thermostat. Sorry I haven't got a pic to show you, but it should be easy to find, it looks like a small Micro switch. Turn off the supply before resetting it though!.
Let's face it, these days if you're not young, you're old - Red Green