This is the first time I have run into this when inspecting a home. The service supply line to the meter is #2 100amp copper. The line from the meter to the service panel is 100amp aluminum. The internal panel has a 200 amp service disconnect. The panel is not overloaded even for 100 amp. My question is should the main service disconnect be 100amp and is this a code violation? Thanks for the help. Larry W.
No, I don't know who did the work, but I was told that the previous owner was a "Contractor". 'nuff said, there was quite a few unconventional things around the house. I can sometimes figure out from looking around what kind of "contractor" someone was, (from what looks good) but then again, sometimes I can't.
Re: Probably a dumb question#22979 03/11/0308:16 AM03/11/0308:16 AM