There is a concern on an existing installation where the meter and outdoor load center are approximately 7 feet from the inside wall of an in ground pool. Looking thru 680 I see no violation, not even a requirement to include it in the equipotential bonding as it is not within 5 feet of the inside wall. Am I correct?
I think you are right but look up. Where is the service drop?
The service conductors are piped across the roof for 25 feet then there is a 90 up with a weatherhead. Adjacent to this weatherhead there is a service mast fastened to the building to support the overhead, keeping it 25' from the water. It is not pretty.
#206920 - 09/01/1205:25 PMRe: Meter & load center proximity to pool
It sounds legal tho... sometimes the law ain't pretty
Was any consideration given to raceways on a roof? (derating)
I doubt it since my area just started enforcing derating for ambient last year, and this installation is at least 30 years old. This brings up something I have been wondering about, when de-rating residential service conductors would you start with the ampacities listed in table 310.15(B)(6)?
#206930 - 09/02/1212:51 PMRe: Meter & load center proximity to pool