Just a slight workspace violation with the metercan on the right side wall of the alcove.... This and the creative feed going to the 2 rightmost meters would never fly here, along with either that door is really short, or that top meter is wayyy above the 6'6" rule we have here..
BTW, while its brought up, why is the gas meter 8' in the air???
Isn't there supposed to be a master disconnect if there's more than 6 meters? ANd shouldn't there be, if it was only 6 meters, disconnects for each service? I'm assuming that the power source is coming in from below.
My first reaction was the proximity of the gas meter as well. I find it hard to believe that the building inspector and/or fire marshall is allowing this to remain as is. Can you say "Building Codes?" Great picture!