Here's some photo's of a home that a new homeowner was just moving into today! He called because one of the ceiling fans wouldn't operate & a couple outlets didn't work.. I asked if he'd had a "home inspection" prior to sale & stated he did!!!! I can't believe someone could miss all these things! Time to play, "Name that code violation!!!"
The emt strap is not so hot, but look at the nail hole in the 2nd & 3rd pics!! Right next to where they don't have a box. This must be his other way of strapping NM cable Is that a 2 screw connector terminating the LT flex in the 1st pic?
Re: Name That Code Violation!#117222 06/05/0405:37 PM06/05/0405:37 PM
Scott, I think its a rigid compression connector, or else its just missing the piece that threads into the LT & the plastic ring that fits on the outside of the LT flex It's half falling out of this connector even though the pic doesnt show it very well...
Re: Name That Code Violation!#117223 06/05/0408:00 PM06/05/0408:00 PM