OK, you asked for pics of jobs so here are a couple I am kind of proud of. This is the day before encasing all these conduits. The main ditch is 8ft below FF and all the resulting set backs are for safety due to the depth of the trench. They are this deep for two reasons. One is to get under a very large footing the other is the fact that after this was all done we had to run two banks of 28 4 inch (each) perpendicular to the runs you see in the pictures and still maintain 24" cover. This was an unusual project for me as I don't work with the tools much these days.I did all the detailing in CAD (coordinating with mechanical and plumbing) and then when the time came, installed all the work with another JW and 2 apprentices. Unfortunately I didn't continue on this job because another project came up and I was pulled to run it. These pictures were taken almost one year ago. (Scott35 and Electure, if you have been in the vicinity of Vineyard and the 60 freeway lately you know where this is.) BTW: This is the main electrical/generator room for a hospital central plant and IT building.
[This message has been edited by electure (edited 04-04-2004).]
nick how much pvc did you run in ft thats look's good it would take week's were i work. nothing but rock in PA anyway i just run underground on my job last week and now i have to go back tommorow. To add 400 ft of 5in for data line's that thay added at the last minute nice work nick
I don't know what the footage is. As you can see this continued on to the chiller rooms, cooling tower yard and boiler room. This work was done in two major phases this being the first. We have a backhoe sub that does allot of electrical underground work. They did s good job on the back fill. I am aways real adamant they don't knock the risers out of plumb. There is nothing worse than spending all this time precisely positioning them to have the backhoe tweak them with a sheep's foot or a whacker. If I remember right this portion took 120 CU yards of 2 sack concrete to cover. They spent two more days backfilling to grade.
Rarely do I come across pipework that I'd consider artistic, with attention paid to the details of lining things up just perfect... Let alone in underground work... Has anyone else ever just stared for a moment after finishing a conduit job thinking... "Damn, that looks nice!" Almost a shame to cover that up! Well done Nick!