Heres a few pics that I took today. The 2 lightpoles are from my daughters daycare parking lot. The rest are from our area ball parks. Funny thing about the ballpark is that while I was there, I noticed smoke rising from the distance. Upon further investigation I found that one of the maintenace buildings had burned down and there was a small pile of rubble still smoldering. From the looks of the wiring around there I would suspect electrical.
[This message has been edited by Webmaster (edited 10-11-2002).]
Pic 1--Feed to scorekeeper rec. pic.2,3,4,5 Service riser and overhead ltg.(no,it's not South America) pic6 this 2 gang bell box and sealtite have been broken for about 2 yrs now pic.7-a new pole was added in this parking lot a year or so ago and this is how the (oops I almost said electrician) idiot picked up a feed for it.Conduit enters thru handhole cover and then about 2 or 3 tubes of silicone seals it up.That wire coming out of the cover also,goes to a ground rod that was added by the pole.
Re: Ballfield Violations #2#113842 10/11/0205:25 AM10/11/0205:25 AM