We have had pictures of pipes through troughs and boxes before. It would never occur to me to do this. First of all because it seems extremely unconventional, but it also seems to be a violation of the listing/labeling of the box. After all, what is the purpose of a junction, or pull box? Also, how would you determine box fill in deciding if the box is large enough to accomodate the pipe, in addition to the wires? I know of no volume allowance associated with various pipe sizes.
Re: new work started out wrong#109122 10/30/0306:25 PM10/30/0306:25 PM
well, it turns out that the red wires are cat 5, and the box is in the way of some things they want to change, but to rewire is so much of a night mare, that they have decided to work around it. Also, whatever they decide on doing will make it hard to have access to either box.
Re: new work started out wrong#109123 10/30/0306:44 PM10/30/0306:44 PM
The raceway through the box although not a usual installation is IMO permissible. I have not found it yet, but there is some language in the code about this very type of installation. Box fill is according to the actual space the pipe occupies. Why does it always seem that our work winds up in one little corner of these big buildings ?