What's there to be bonded?
Check with your AHJ first, but the equipment grounding conductor run with your power source should be suffice to bond the motor.
I had an AHJ once ask me to run a solid #8 copper from the motor ground lug to a sub panel in the attic. The motor wasn't installed last time I was there and I haven't been back since so I don't know if it was ever installed. I sure wish I could ask him what article he was quoting.