Posted By: Trumpy
Water in UG Service - 06/22/06 10:53 AM
Pics and info provided by e57:
Check existing service equipment at remodel. Looked around to actually find it... It was in a dog-house under an over-hang of the house, had to crotch to get to it. I open the dog-house door, and see a note to POCO, "Water comes out of meter, what should we do?" I think, well that a strange note? Lets open up and take a look.... I start at the main, which is above the meter.... Well what do you know, water in ther too, and an attempt to correct the problem by filling conduit with foam. I don't think I want to open the meter now.... Also notice that there is NO GEC at all, no rods, no water... and the main has two 2" KO's missing. I call this a "Just start over Service"