You might want to pull it for testing purposes.
If you are looking for illegal ground to neutral connections lifting the neutral would be step one along with the MBJ.
That said I don't understand what it really accomplishes, I have never seen any one in the field talk about it. It seems more of a construction specification of service rated equipment. 225.36
Now when we use the exception to 225.36 do we need to use two pole snap switches so we can break both grounded and ungrounded conductors simultaneously?
FWIW 225.38(C) mirrors 230.75