okay i give up...i know that somewhere it's in the nec, but i don't know where to find the article that tells us that dead wiring must be removed, or safed off properly. i'm fighting with an owens corning basement finishing contractor about having dead ckts. behind the walls.
after much searching i found the article in the nj fire code...we (electrical) are responsible for enforcing parts of other subcodes here in nj. the fire official stered me to the right article in his code.
Re: de-energized wiring#99644 08/26/0605:45 AM08/26/0605:45 AM
on the rough i found the cables and j boxes behind studs set off 6" from the basement walls, they were live at the time of the rough. i explained to the contractor that they were to be removed..he did not comply, he said that the "owens-corning" system was "accessible"....and the rest is history