Yup its 440.65. not 440-65, reminds me of star trek ( star date 440.65...)
ok, lemme read this to you here... Single-Phase cord & plug connected room air conditioners shall be provided with factory-installed LCDI or AFCI protection. The LCDI or AFCI protection shall be an integral part of the attacthment plug or be located in the power supply cord within 300 mm (12 in) of the attatchment plug.
What is a LCDI ?
Has anyone seen one in breaker form?
What if the circuit already has AFCI protection?
Would this take the place of AFCI protection in a bedroom dedicated AC circuit?
What next, AFCI for dryer circuits to address static cling?