I just purchased a new Kenmore oven and the manual calls for a minimum of 8 Gauge solid copper on a 40 Amp circuit. I went to Home Depot and purchased 60 ft. of 8-3 with ground. When I got home I noticed that it is NOT solid copper but stranded copper. Will this matter? the manual specifically calls for solid. should I worry about it or is it ok since it will be on a 40 Amp breaker?
Just bought the place and don't want to burn it down! (wife would be angry) Thanks.
It sounds like you are unfamiliar with this situation and would no doubt be better off with some help in this. I would suggest that you contact someone locally that is Licensed/Certified and capable of handling this. Everyone will sleep better at night.
Hmm... back to Home Depot I go! Good thing you can return cut wire there...
I didn't take distance into consideration when I read the owner's manual. Now that I think about it I know 6 will be a better choice. I am installing this into an 1950 house and the gap between the plaster and cinder block is only about an inch so I was worried about the wire being to big to install. I am going to install this in conduit because of this.
Although 8 on a 40 would have been safe... I don't want to be tripping breakers while trying to cook dinner.