The UL White book receptacle section (RTRT) says: "Terminals of the wire-binding screw, setscrew, or screw-actuated back wired clamping types are suitable for use with both solid and stranded building wires. don(resqcapt19)
[This message has been edited by resqcapt19 (edited 05-15-2001).]
Re: Device Termination for stranded#77217 05/15/0107:57 AM05/15/0107:57 AM
Ideal makes these forked terminals that are on the end of a little blue wire nut. They're much cheaper than crimp type, easier to use and look a lot better too. I use them if space permits, otherwise I use the ol' trick Steve mentioned.
[This message has been edited by sparky66wv (edited 05-15-2001).]
-Virgil Residential/Commercial Inspector 5 Star Inspections Member IAEI
Re: Device Termination for stranded#77219 05/15/0101:11 PM05/15/0101:11 PM
I was always told to have the wire inserted with the turn of the thread ( clockwise ) and that would eliminate the insert from 'right side' comment. Of course if the binding screw is 'counter clockwise thread' that would be a different story.