Make your outlets as high as you wish. Between 18 and 72 inches usually suits me. Might your basement flood?
Personally I would put in a GFCI breaker and run the basement lights from that. You can also daisy chain through a GFCI receptacle which is cheaper by about $29 assuming that you still have to buy a single regular breaker.
You didn't say what loads (laundry?) you will have or how big it is.
Several separate circuits may be in order. Is the load center in the basement?
Keep in mind that many tools are 9-15 amps. One 20 amp circuit doesn't go very far when you start plugging big things into it.
Make sure all unfinished basement outlets are GFCI protected.
An unfinished area to me means that there is not padded carpeting wall-to-wall or girders or metal pipes are exposed.
You don't ever want water to get into your GFCI devices.
[This message has been edited by Dspark (edited 05-10-2001).]
Re: electrical work in basement#77180 05/10/0108:20 PM05/10/0108:20 PM
There's already a circuit for the washer and dryer. I don't think I should be using it anyway. Or can I?
No, let it alone. The laundry circuit should be dedicated under the current code. Yes, go with the GFCI, even in the lights if possible. Though someone my mention that fluorescents could cause nuisance tripping, I have not found that to be the case with the new electronic (instant start) balasts.
Re: electrical work in basement#77186 05/12/0106:54 AM05/12/0106:54 AM
I think I should use a different circuit for the light and the outlet so I don't loose the light if my outlet gets shorted.
This is always a good Idea. As far as the lighting on the GFCI, That's got to be your call. As Dspark says it will give you more personal protection fron shock, but if the lights go out on you (nuisance tripping) will that pose another type of hazard? Only you know the circumstances of your room layout and it's probable usage.
And, yes, new circuits would be called for. An inspection (by Electrical Inspector or consultation with a Licensed Electrician) is always recommended for your personal safety and it could save you money. If you do not do things according to code rules you may end up having to tear things apart later on. I see it happen all the time!