Math 40 circuit panel....20 amp, 1 pole cb's
800 amps; divide by 2 hot legs (resi)= 400 amp max connected load. BUT, the 200 amp main would trip.
Load calcs are in the NEC
Theory is you can have an unlimited quantity of "sub-panels", the limitations are the OCP of the main, and the OCP of the feeders.