aldav53...Jus noticed your in Arizona...gets real hot up there in those attics out there.
Be sure to apply the ambient temperature correction factors for the wiring up in that there attic. You could use a correction factor that would cut the ampacity of the wiring by 50%
Find this info below table 310.16 NEC...
You would be better off to run underground to that garage.